Use and maintenance of customized ISW Horizontal Inline Pump
The use of customized ISW Horizontal Inline Pump
(1) Start of customized ISW Horizontal Inline Pump
1. Before starting the customized ISW Horizontal Inline Pump, check whether the bolts at each fastening part are loose, whether there is abnormal noise, and whether the oil quantity of the lubricating part is sufficient, etc., and eliminate possible problems as soon as possible to avoid losses.
2. The customized ISW Horizontal Inline Pump should be filled with water before starting. Before filling, unscrew the vent plug, then add water until water emerges from the vent hole, and then turn the pump shaft a few times.
(2) Operation and stop of customized ISW Horizontal Inline Pump
1. Precautions when running customized ISW Horizontal Inline Pump. Pay attention to the operation of the power machine, and observe whether the water temperature and oil temperature are normal; pay attention to the sound and vibration of the unit. When the unit vibrates too much or there is a noise, it is often a signal that the water pump is faulty, and it must be shut down for maintenance to eliminate hidden dangers; whether there are floating objects at the water inlet, Whether the submerged depth of the bottom valve is sufficient; whether the fastening parts are loose, and whether the joints of the water inlet pipe are tight and air-tight.
2.Customized parking of ISW Horizontal Inline Pump. When the pipeline pump is stopped, the water outlet valve should be slowly closed, and the speed of the power machine should be gradually reduced to make it in a light load state, and finally the power machine should be stopped.
Maintenance and maintenance of customized ISW Horizontal Inline Pump:
1. Clean the surface of the pump frequently.
2. For those lubricated with oil, replace the oil every 1 month; for those lubricated with butter, replace the butter every six months.
3. Avoid pumping and draining muddy water with too much sediment, otherwise the impeller, mouth ring, packing, etc. will be easily worn.
4.Customized ISW Horizontal Inline Pump should be overhauled before storage in winter, and its scope includes power machine, transmission equipment and electrical equipment.